HANNOVER MESSE 2019,
01 - 05 April
The basic principle for surge protection is the complexity and coordination of protections. The complexity requirement can be met only by installing surge protections in all inputs and outputs (!) of the given equipment, i.e. it is necessary to protect the feed line, measuring and communication interface. We can ensurecoordination by installing protections with various protective effects in sequence intothe line or the communication core and the interface.Criteria to meet the requirement for complexity and coordination particularly include installation position or zone boundary, maximum pulse or discharge current, required protection level and response time.In order to select the correct type of protection for light-current signals, you must also have detailed information on the protected signal:a) Signal voltageb) Signal currentc) Frequency bandwidth - frequency and signal formd) C onduit in lightning protection zones (LPZ 0 to LPZ 2)e) L ongitudinal impedance - maximum line attenuationf ) Possibility of steady overvoltage (so-called high-ohm fault)
Visual fault signalling SPD Type 3
Combination of varistor surge protection and an encapsulated spark gap. To be installed in low-voltage distributions at the ...
Replaceable module, visual fault signalling
Combination of varistor surge protection and an encapsulated spark gap connected in the mode 1+1. To be installed in ...
Encapsulated high-performance spark gap
To be installed in low-voltage distributions at the boundary of LPZ 0A and LPZ 1 zones to prevent overvoltage effects induced ...
Principles of positioning and wiring of surge protections and lightning current arresters
Surge protections and lightning current arresters cannot be installed ...