HANNOVER MESSE 2020,
20. - 24. April
MEgA - Merici Energeticke Aparaty
The communication unit MEg202.5 in its basic configuration provides remote transmission of states or changes of binary inputs and commands by GSM / GPRS, UMTS / HSPA and LTE networks of mobile operators. The measured values are transferred through the serial communication line RS485 from connected measuring devices.
The unit installed in the station technology can be connected through two RS485 serial interfaces and it implements the standardized communication protocol according to EN 60870-5-104:2006 and allows integration of connected devices into the SCADA system, either directly or through concentrators. The units has a processor that optimizes and controls data transmission, communicates with connected devices through technological network, allows pre-processing of data read from measuring devices, supervises connected devices and automatically transmits data to a host system in case of an event.
The MEg202.5 unit can be used also in the function of a communication converter GPRS / UMTS / HSPA / LTE on RS485 bus when the data sent through the mobile operator network are re-sent in transparent mode to the programmed RS485 channel and conversely, the data from RS485 are sent back.
RTU communication unit for GSM networksLTE, UMTS, HSPA+, GPRS, EDGE
2x RS485, USB, SIM
5 galvanically non-separated inputs
2 galvanically separated relays
event-driven data transmission
power supply 12 VDC to 24 VDC
DLMS, MODBUS, IEC 104
54x90x63 mm, 0.2 kg
The MEg44 class S PQ monitor measures three voltages and three currents of the DTS transformer at LV level. It provides the functions of recording, electricity meter ...
The portable multiple input PQ monitor MEg37 measures four voltages and the total of 36 currents at the LV level. It provides the functions of measuring and evaluation ...
The fuse state indicator MEg72 is used for local and remote indication of the fuselink with knife blade contacts in LV grid. It enables you to identify the states ...
The measuring rail MEgML73 is intended for sensing phase voltages and phase currents of LV fuse and disconnector rails for measuring instruments with current and ...
The output feeder monitor MEg71 is intended for measuring voltages, currents, powers and energies of a LV output feeder of a switchgear with fuse rails or fuse disconnectors. ...
PQ monitor MEg39 measures four voltage and four current values at LV, MV, HV levels. It provides the functions of recording, electricity meter and analysis of voltage ...
The portable PQ monitor MEg38/C is intended for measuring and recording of four voltages and four currents, active and reactive powers and energies in three-phase ...
The MEg70 compact phase monitor is characterized by mechanically associated measurement of voltage, current, measuring and evaluating circuits including a serial ...
The communication unit GPRS MEg202.2 in its basic version provides remote transmission of states or state changes of binary inputs and commands through the GPRS ...
The split core current transformer SMART PTD is installed in LV networks on to live and insulated wires. In its operating state the transformer is characterized ...
The communication units MEg201.5 with RTU functions provides remote transmission of states of binary inputs, commands and measured data from connected instruments ...
Auf der Merkliste